EXAMPLE: To replace a 55 + 4 microfarad
Dual-Value Capacitor: BEFORE YOU START: Make note of the wires which are
attached to the fan motor (F), common (C), and compressor (Herm) terminals of
the capacitor being replaced. STEP 1: To achieve the 55 microfarad for the
compressor (HERM) - using two (2) jumper wires (a) connect the 10 + 20, then
(b) connect 20 + 25, This will equal 55.0
microfarads. Connect one of the wires from the compressor to the 25 MFD
terminal. STEP 2: Connect the other wire(s) from the compressor to the common
(C). [The common is the center black terminal]. STEP 3: Connect one of the fan wires to the 5 (4) mfd
terminal. STEP 4: Connect the other wire from the fan motor to the common (C).
[The common is the center black terminal].