EXAMPLE: To replace a 15 + 7.5
microfarad Dual-Value Capacitor:
BEFORE YOU START: Make note of the wires which are attached to the fan
motor (F), common (C), and compressor (Herm) terminals of the capacitor
STEP 1: To achieve the 15 microfarad for the compressor (HERM) – Using one (1)
jumper wire, connect the 5 (6) + 10.
This will equal 15 microfarads.
STEP 2: Connect one of the wires
from the compressor to the 10 MFD terminal. STEP 3: Connect the other wire(s)
from the compressor to the common (C). [The common is the center black
STEP 3: To obtain the 7.5 microfarad for the fan (F), using one (1) jumper
wire connect the 5 (4) + 2.5 (3.0) . This will equal 7.5 microfarads. STEP 3:
Connect one of the fan wires to the 5.0 (4.0) MFD terminal.
STEP 4: Connect the other wire from the fan motor to the common (C). [The
common is the center black terminal].