To replace a 20 + 3.0 microfarad Dual-Value Capacitor: BEFORE YOU START:
Make note of the wires which are attached to the fan motor (F), common (C), and
compressor (Herm) terminals of the capacitor being replaced. STEP 1: To achieve
the 20.0 microfarad for the compressor (HERM) - Connect one of the wires from
the compressor to the 20 MFD terminal. STEP 2: Connect the other wire(s) from
the compressor to the common (C). [The common is the center black terminal].
STEP 3: Connect one of the fan wires to the 2.5 (3.0) MFD terminal.
STEP 4: Connect the other wire from the fan motor to the common (C). [The
common is the center black terminal].