EXAMPLE: To replace a 25 + 12.5
microfarad Dual-Value Capacitor: BEFORE YOU START: Make note of the wires which
are attached to the fan motor (F), common (C), and compressor (Herm) terminals
of the capacitor being replaced. STEP 1: To achieve the 25.0 microfarad for the
compressor (HERM) - Connect one of the wires from the compressor to the 25 MFD
terminal. STEP 2: Connect the other wire(s) from the compressor to the common
(C). [The common is the center black terminal]. STEP 3: To obtain the 12.5
microfarad for the fan (F), using one (1) jumper wire connect the 2.5 (3.0) +
10. This will equal 12.5 microfarads. STEP 4: Connect one of the fan wires to the 10.0 MFD
terminal. STEP 5: Connect the other wire from the fan motor to the common (C).
[The common is the center black terminal].