EXAMPLE: To replace a 40.0 + 4.0 microfarad
Dual-Value Capacitor: BEFORE YOU START: Make note of the wires which are
attached to the fan motor (F), common (C), and compressor (Herm) terminals of
the capacitor being replaced. STEP 1: To achieve the 40.0 microfarad for the
compressor (HERM) - using two (2) jumper wires (a) connect the 5 (6.0) + 10,
then (b) connect the 10 + 25. This will equal 40.0 microfarads. Connect one of
the wires from the compressor to the 25 MFD terminal. STEP 2: Connect the other
wire(s) from the compressor to the common (C). [The common is the center black
terminal]. STEP 3: Connect one of the fan wires to the 5 (4) MFD terminal.
STEP 4: Connect the other wire from the fan motor to the common (C). [The
common is the center black terminal].