EXAMPLE: To replace a 40 + 7.5 microfarad
Dual-Value Capacitor: BEFORE YOU START: Make note of the wires which are
attached to the fan motor (F), common (C), and compressor (Herm) terminals of
the capacitor being replaced. STEP 1: To achieve the 40.0 microfarad for the
compressor (HERM) - using two (2) jumper wires (a) connect the 5 (6) + 25, then
(b) connect the 25 + 10. This will equal 40.0 microfarads. Connect one of the
wires from the compressor to the 25 MFD terminal. STEP 2: Connect the other
wire(s) from the compressor to the common (C). [The common is the center black
terminal]. STEP 3: To obtain the 7.5 microfarad for the fan (F), using one
(1) jumper wire connect the 5 (4) + 2.5 (3.0). This will equal 7.5 microfarads.
STEP 4: Connect one of the fan wires to the 5.0 (4.0) MFD terminal. STEP 5:
Connect the other wire from the fan motor to the common (C). [The common is the
center black terminal].